Warning: All wiring should be installed by a trained and qualified electrician. Wiring must conform to all applicable local codes and regulations.
- Adhere to IEEE 1100 specifications for grounding.
- Do not exceed a 40 percent fill for conduits.
- Route the conduit away from
power trays using these guidelines:
6 in. 110 VAC 12 in. 220 VAC 24 in. 440 VAC
- Attach the conduit to the NPT threaded holes on the side of the CSI 9420.