The Trex unit can power one FOUNDATION fieldbus device. The Trex unit can provide approximately 10 volts at 25 mA to power a FOUNDATION fieldbus device. (The Trex unit will draw approximately 12 mA when it is online)
If you try to apply power from the Trex unit when the device is externally-powered, the Fieldbus Diagnostics application prevents the Trex unit from supplying power. This protects the Trex unit from damage.
- Connect the lead set to the FF terminals on the Trex unit and directly to the communication terminals on the unpowered device. Ensure no other wires are connected to the device and there is no power to the device. Do not attach to a junction box.
Connect the FOUNDATION fieldbus Power Plug to the FF pwr terminal
and the positive (red) terminal on the lead set.
Connection for powering a FOUNDATION fieldbus device
- FOUNDATION fieldbus Power Plug
Fieldbus Diagnostics Overview screen, tap
Power Supply to enable power to the device.
The Trex unit powers the device.
- To stop power, tap Power Supply or disconnect the lead set from the Trex unit.